Published at Thursday, May 31st, 2018 - 08:02:13 AM. . By Genevieve Rust.
How to Resolve the Humidity: First step should be the installation of a vapor barrier around the entire room. A minimum of 4 mil plastic is recommended with seams overlapped and taped. The vapor barrier is installed on the outside (or warm side) of the cellar insulation. This is to prevent condensation from forming on the vapor barrier, potentially causing mold. A cooling unit alone cannot add moisture or humidify cellar air. It needs a humidifier to do so. The best option is a humidifier integrated into a cooling unit so it operates and distributes the moisture evenly in the re-circulating air. However, a free-standing humidifier can also be installed in conjunction with a cooling unit as long as this is controlled by a high-quality wall-mounted thermostat.
The Wine Room: Before installing a wine refrigeration system, make sure the room is vapor sealed and properly insulated. Every wall and ceiling should be scaled with a vapor barrier on the "warm side" of the walls. 6 or 8 mil plastic sheeting is highly recommended. Interior walls should be insulated to a minimum of R-19. We recommend using rigid foam board. Additionally, all cracks should be filled with expanding spray foam. All walls are finished with moisture resistant green board.
Any content, trademark’s, or other material that might be found on the Beer Hyped website that is not Beer Hyped’s property remains the copyright of its respective owner/s. In no way does Beer Hyped claim ownership or responsibility for such items, and you should seek legal consent for any use of such materials from its owner.
© Copyright 2018 Beer Hyped. All Rights Reserved.